YES… sort of… perhaps. The National Fuel Gas Code does not ban galvanized piping in gas installations, unless a current edition has amended this. Yes, zinc flaking is a worry, but it’s no more so than copper sulphite resulting from reactions between contaminants in the fuel and copper in the system. This is why each appliance requires a properly placed sediment trap (also known as a drip leg).
What kind of propane pipe is used?
- Black pipes are tough and long-lasting. Black steel pipes, black iron pipes, and black malleable pipes are some of the other names for them.
- Natural and propane gas is transported from the street or a tank to the home using this device.
- It’s available in lengths ranging from 2 inches to 10 feet, with diameters ranging from 1/4 inch to 2 inches.
Is it possible to use black pipe for propane gas?
Running black iron pipe for propane use may appear to be a difficult process, and you will pay a professional to complete it. The truth is that this is a great do-it-yourself project if you have the necessary tools and some basic pipe fitting knowledge.
This can be done in an afternoon depending on how much pipe needs to be installed, potentially saving you hundreds of dollars in installation fees.
What is the most typical material for propane piping in the home?
Many households in the northern half of the country will have to turn on their heating systems at the beginning of October. Natural gas is one of the most cost-effective and efficient fuels for a furnace or boiler. With its benefits come questions about safety and obligations for homeowners. It is your role as a home inspector to assist in the detection of flaws that may jeopardize the safety of residents in natural gas-powered homes. We’ll go through some of the fundamentals of gas piping inspection.
The gas supply line, also known as the building line, is the plumbing that runs throughout the house. Individual appliances are served by branch lines. The branch line finishes in a drop line, which is a vertical pipe that drops down from an overhead branch line to the appliance. If it carries gas up to an appliance from a branch line below the appliance, it’s called a riser.
A sediment trap or dirt pocket, commonly referred to as a drip leg, is normally present at the appliance connection point and consists of a nipple and a cap. This pipe extension, which is normally at least 3 inches long, is designed to catch any water or foreign material that may be present in the gas before it enters the appliance. The solids and liquids fall into the pocket, which is just a gravity mechanism.
The homeowner is normally responsible for the pipework downstream of the gas meter. The gas company is normally responsible for the piping upstream of the gas meter, as well as the meter itself.
Steel, copper, and brass are the most popular materials for gas piping. In some cases, galvanized steel, copper, brass, or CSST (Corrugated Stainless Steel Tubing) can be used, but copper is prohibited by some utilities. Copper is widely used in different parts of the world. You should be aware of what is considered acceptable in your neighborhood. Black steel piping with malleable iron or steel fittings is common. In other cases, galvanized steel is also used.
Flexible connectors are allowed to be used to connect appliances to gas pipelines. A shut-off valve must be installed at the rigid piping connection. This valve must be located in the same area as the appliance.
Accessible and three or six feet long: The flexible connectors cannot pass through walls, floors, or ceilings, and they cannot be hidden. Except for gas stoves and laundry dryers, the flexible connector length is normally limited to 3 feet. 6 feet is usually allowed for these equipment. Using nipples to splice or join connectors is frequently forbidden. Flexible connectors are only allowed in some jurisdictions for gas stoves, dryers, outdoor barbecues, and other semi-portable equipment. Flexible connectors may be prohibited on gas furnaces, water heaters, space heaters, and other similar appliances. Flexible connectors are more likely to be utilized on all appliances in earthquake-prone areas because they give some protection against gas piping leakage or rupture during an earthquake. To find out what is and isn’t permitted in your area, consult your local gas code.
The use of white thread seal tape (often referred to as Teflon tape) as a connecting compound for steel gas piping is not recommended. Cutting oils on the pipe threads from the manufacturing process may hinder the tape from sealing. Yellow thread seal tape is permitted in some regions. Pipe dope is favored and may be the only option available. You might wish to double-check with the gas company. Inquire about whether any piping installations with thread seal tape of any color should be reported as a defect.
Although certain exceptions exist, most appliances should have a shut-off valve nearby.
The use of gas piping as a grounding mechanism for the electrical service is prohibited by most authorities. In many countries, however, bonding the gas piping to the electrical grounding system is required. This is often accomplished by connecting the gas pipe to the supply water piping (assuming it is grounded) near the water heater. We want to keep the gas piping at zero electrical potential by attaching it to the grounding system to prevent an electrical potential building within it that could lead to arcing, which could ignite gas.
All of these issues have the potential to result in gas leaks and explosions.
Carson Dunlop’s home inspection training program is the only certified college dedicated solely to house inspection training and is designed to ensure your success. For more information about Carson Dunlop’s home inspection training program, click here.
What is the composition of propane lines?
The service plumbing, also known as the yard line, is the gas line that travels between the tank and the structure that houses the gas appliances. Copper tubing or plastic polyethylene piping are commonly used in propane yard lines. For the entire exterior section of the installation to be safe and serviceable, the service piping must be installed appropriately and legally in conjunction with the propane tank.
The visible portion of the yard line is where it emerges from the ground adjacent to the tank, as well as where it enters the structure or links to a source of usage, such as a generator or pool heater. For any section of a propane gas service line, only certified materials and fittings should be utilized. PVC, rubber hose, and flex lines are prohibited and should not be utilized in any component of the gas service line.
Is it possible to utilize PEX pipe for propane gas?
PEX pipe is not the same as PE piping, and the two are frequently confused. Polyethylene, or PE, is a flexible plastic polymer that is ideal for piping in wells and other cold-water supply lines.
PEX stands for polyethylene that has been cross-linked. It’s made of polyethylene, a material with a stronger link between the polymer chains that make it up. PEX is now suited for both hot and cold water applications as a result of this advancement. It can also be utilized in some gas applications, depending on the building code.
PEX and PE are more flexible and have a significantly greater pressure rating than typical gas lines, thus they suit those requirements. They are, however, made of a soft material that could be damaged by nails, rodents, and other objects. As a result, in your location, either may not be permitted for use as a residential gas line. Even when the utility provider is able to install it, plumbers and homeowners are not always able to.
Is it okay to run a gas line via galvanized pipe?
Because of the galvanized coating, you should not use galvanized pipe for gas. Galvanized steel bits will flake off over time and block your gas regulators and burner units. If you mix galvanized and black iron, corrosion will be accelerated where they come into contact.
Is black pipe or galvanized pipe more durable?
The two most prevalent types of pipe used to convey liquid and gas are black steel pipe fittings and galvanized steel pipe fittings. Although both black steel pipe and galvanized pipe are constructed of steel, galvanized pipe has a zinc coating and black pipe does not. As a result, galvanized pipe is more resistant to corrosion. Because black steel pipe erodes more rapidly than galvanized pipe during transit, it is better suited to transferring gas, while galvanized pipe is more suited to conveying water.
Galvanized pipe fittings are coated with a coating of zinc, which increases their corrosion resistance and helps to prevent mineral deposits from clogging the pipe. Galvanized pipe is mostly used to transport water to homes and businesses; but, due of its rust resistance, it can also be utilized as scaffolding frameworks.
Because of the material’s ability to resist corrosion and salt, galvanized pipe fittings are employed in a variety of outdoor and industrial applications. With the exception of underground lines, galvanized pipe and fittings can be utilized in most applications. They operate best with cold water lines, although they can also be used with hot. When opposed to black and copper fittings, the key advantage of employing galvanized fittings is their better rust resistance. With gas applications, galvanized pipe fittings should not be utilized.
Connections to black iron pipe are made with black pipe fittings (black malleable iron fittings). In residential applications, black iron pipe is used to deliver natural and propane gas.
Because black steel pipe is created as a seamless product, it is a superior choice for gas transmission and fire sprinkler systems than galvanized pipe. Due to its strong heat resistance and resistance to water damage, black iron pipe is commonly used in fire sprinkler systems and water supply lines. It’s named black steel pipe because of the dark hue it has on the surface, which is caused by iron oxide during the production process.
The surface difference between steel and galvanized pipe is the most significant. Because black steel pipe is uncoated and manufactured without steam, it is extensively utilized to transmit gas such as propane and natural gas to homes and businesses.
Because zinc is present on the surface of galvanized pipe, the mineral will flake off over time and clog the pipe. There will be a burst as a result of this. As a result, transporting gas through galvanized pipes is hazardous, hence it is frequently used to transport water.
On the other side, black steel pipe is not appropriate for water transport. Black steel pipes corrode with water, and the minerals in the pipe dissolve in the water, clogging the line.